You can have up to 4 products listed for comparison
A generator can help restore life to normal during emergencies, but its safe use requires care and planning. For example:
- Always thoroughly read the manufacturer’s instructions. This can help avoid dangerous shortcuts and assist you in ensuring safe operation of your generator and prolonging product life.
- Keep generators away from all open windows – including office or even home windows or door ways – so deadly exhaust does not enter the home or business.
- Be a best practice person. Consider that the sound of your generator may not be music to everyone’s ears! Generators can be 99DBA at 1m for a 700kVA set.
Here are some additional guidelines and more specific tips for those using portable generators and for those using stationary generators.
petrol-powered generators produce deadly carbon-monoxide fumes.
- Always run portable generators outside the building.
- Never run generators inside, or in a garage.
- Keep generators well away from open windows – including neighbors’ windows or office windows – so deadly exhaust does not enter the property.
Never connect a generator directly to your home’s wiring. Power from a generator connected to a home’s wiring will “back feed” into national grid, potentially injuring severely or killing a neighbor or electrical crew working to restore service. Either:
- Plug appliances directly into the generator’s outlet.
- Use a heavy-duty extension cord rated for outdoor use to keep the generator safely outdoors. If the appliance has a three-prong plug, always use a three-prong extension cord.
- Follow the manufacturer’s recommendations for earthing the generator, Generator earthing rods are low cost items but are a must!
- Hire a licensed electrician to connect the generator to your house wiring using a “listed” transfer switch, which means it meets nationally recognized safety standards as indicated by the UL Listing Mark on the product. Having an electrician install the listed transfer switch will safely prevent your generator from back feeding utility lines, thus avoiding a safety hazard to you, your family, neighbors and utility workers, and preventing possible damage to your generator when utility power is restored.
Tip: You don’t need to run everything at the same time; rotating larger items allows the use of a smaller generator, which costs less to buy and is easier to move.
Maintenance tip – remove your generator from storage, drain the fuel from the fuel tank (safely) and dispose of it properly following all local regulations on safe disposal of waste fuel/oil. Inspect the fuel line for cracks and replace if necessary. Refill the tank with fresh fuel and run the generator. Add some appliances, e.g., a trouble light, hair dryer, etc., to make sure the generator is operating properly.
After the generator has warmed up (about 15 minutes of running), turn off the fuel valve and run the fuel line dry. After the engine stalls, turn off the run switch, change the oil, add fuel stabilizer to the gasoline, drain the carburetor and put the generator back in storage once it has fully cooled down. While you are testing the generator, inspect your extension cords to make sure they’re in good condition. Replace any cord that has damage or showing signs of wear and tear.
If you had any trouble with the generator during this test, call us on 0800 978 8988 as we offer servicing or email email@example.com
- Never refuel a hot generator or one that is running; hot engine parts or exhaust can ignite gasoline.
- Turn off all connected appliances before starting your generator.
- Turn connected appliances on one at a time, never exceeding the generator’s rated wattage.
- Save gas by using appliances only as needed. If no appliances are running, shut the generator off.
- If you’re just running a few lights, using other sources may cost less than running the generator.
- Don’t leave a running generator unattended; turn it off at night and when away from home.
Tip: Refrigerators may only need to run a few hours a day to preserve food. Using a refrigerator thermometer, aim to maintain 40 degrees in the refrigerator compartment and 0 degrees in the freezer.
When storm season is over, properly store your generator so it will be ready to go next time and every time when you need it.
To store a generator until next season:Fill the tank with fresh gasoline or completely drain the tank. Add the proper amount of fuel stabilizer if storing it with fuel, noting the go “off” date. Drain the carburetor float bowl. Drain the sediment cup (if one is installed). Change the engine oil if needed.
Stationary generators rely on an automatic transfer switch that senses when power has been interrupted and automatically starts the generator. Conversely, when power has been restored, the generator powers off.
Exercising – Stationary (permanently installed) generators should be exercised at least twice each month for 15 to 20 minutes at a time. It’s best to exercise the generator with at least 40 to 60 percent of its maximum load. If the testing is less rigorous than this, then it should be operated annually on a load bank for an extended period (see below).
Load bank testing – This is usually done at the same time as the oil change, if the generator is not tested at least twice per month with the manufacturer’s recommended minimum load. It is recommended to load test the generator once per year. The following are the recommended test lengths.
Generator output Length of 100% load bank test
100 kW and less 1 hour
100 to 200 kW 2 hours
200 kW and larger 4 hours
Diesel fuel will deteriorate with age. Under normal conditions, diesel fuel will last approximately two years but the use of bio fuel is bringing this figure down. For this reason, the storage tank should be sized so that normal maintenance and testing will use up the fuel within that period. If fuel is stored for longer periods, or in high-moisture areas, a fuel additive can be used to extend fuel life. The additive is a microbicide that will slow the growth of fuel microbes that can plug fuel filters and damage engines.
LPG (liquefied petroleum gas) – This type of gas requires on-site storage. It can be stored indefinitely. The frequency stability of spark-ignited engines is not as good as diesel. This may be a consideration when using the generator to serve loads that are frequency sensitive such as uninterruptible power supplies.
Natural Gas – Natural gas does not require on-site storage. It does have the same frequency stability problems that LPG has.
Service – Stationary generators should be looked at and, if necessary, serviced twice each year. One visit should include a thorough inspection, including system diagnostics. The other visit should include a thorough inspection, including system diagnostics, an oil change and the replacement of both the oil and fuel filters.
Stationary generators work in tandem with your electric supply in a virtually seamless operation. As convenient as these generators are, a prudent course of action is to always be prepared in the event of an emergency, particularly an extended power outage.